Our knowledge base offers advice, help and answers to those commonly asked questions such as 'how do i install a wood burning stove' or 'whats the difference between a wood burner and a multifuel stove' as well as offering useful tips on using a stove and stove maintenance.
Use our search facility to locate the specific topic you are looking for or select a category heading for a list of related topics.
If you have a specific question that you cannot see answered here please contact us and we will endeavour to answer your stove question ASAP.
If the output of your stove is greater than 5kW then you do need permanent ventilation to the room. There is no stipulation in the building regulations as to the type of vent that must be used however examples would be air bricks, core drill vents etc. We stock a range of HETAS approved air vents in the
For stoves with outputs over 5kW the free area requirement of the vent is 550mm² per kW over and above 5kW. So an 8kW appliance would have a free air requirement of 1650mm². The amount of ventilation required does vary for other types of appliance such as open fires or stoves with flue draught stabilisers, please contact us or your HETAS approved installer for advice.
A sufficient air supply for a solid fuel fired appliance is very important. It ensures that complete combustion of the fuel occurs and also allows the chimney to function correctly. An insufficient air supply can have serious consequences. Smoking will occur and also increased levels of carbon monoxide will be produced which can be life threatening.